目录

简介

先决条件

要求

使用的组件

规则

背景信息

配置

网络图

配置

验证

相关信息

简介

本文为在 Catalyst 3750 系列交换机上配置和验证 Cisco EnergyWise 功能提供一个示例。本文特别向您介绍如何在 Catalyst 3750 交换机上配置 Cisco EnergyWise 功能。

先决条件

要求

尝试进行此配置之前，请确保满足以下要求：

- 具有 Cisco Catalyst 3750 系列交换机的配置基础知识

- 具有对 Cisco EnergyWise 功能的基本了解

使用的组件

本文中的信息基于 Cisco Catalyst 3750 系列交换机。

本文档中的信息都是基于特定实验室环境中的设备编写的。本文档中使用的所有设备最初均采用原始（默认）配置。如果您使用的是真实网络，请确保您已经了解所有命令的潜在影响。

规则

有关文档约定的更多信息，请参考 Cisco 技术提示约定。

背景信息

Cisco EnergyWise 是提供监视和控制整个 IT 基础设施电源的能力的电源管理功能。Cisco EnergyWise 提供一个框架，网络本身可由此框架用于打开所有设备类型的电源管理。

Cisco EnergyWise 域是用于电源监视和控制的设备管理分组。支持 EnergyWise SDK 客户端的 Cisco EnergyWise 终端响应从管理应用或使用 Cisco EnergyWise 协议的其他域成员发起的 EnergyWise 查询。

配置

在此部分中，将为您提供配置本文所述 Cisco EnergyWise 功能所需的信息。

注意：要获取有关本部分中所使用命令的更多信息，可使用命令查找工具（仅限已注册客户）。

网络图

本文档使用以下网络设置：

配置

本文档使用以下配置：

Catalyst 3750 交换机

configure terminal

!--- Enable Cisco EnergyWise on supported platforms.

Switch(config)#energywise domain Cisco security shared-secret 0 cisco protocol

udp port 43440 ip 10.78.4.48

!--- Set the EnergyWise importance for the platform.

Switch(config)#energywise importance 80

!--- Set the EnergyWise keywords for the platform.

Switch(config)#energywise keywords lab1,lab2

Switch(config)#service password-encryption

!--- Enable communication between management applications which support EnergyWise protocol and domain.

Switch(config)#energywise management security shared-secret 7 070C285F4D06 port 60500

!--- Set the EnergyWise name for the platform.

Switch(config)#energywise name floor.lab

!--- Configure a static neighbor.

Switch(config)#energywise neighbor 2.2.4.31 43440

!--- Set the EnergyWise role for the platform.

Switch(config)#energywise role access4lab1

Switch(config)#energywise allow query save

!--- Configure Cisco EnergyWise on a port.

Switch(config)#time-range onlabfloor

Switch(config-time-range)#absolute start 00:00 01 January 2012 end 23:59 01 Jan 2012

Switch(config-time-range)#periodic weekdays 7:00 to 19:00

Switch(config-time-range)#periodic weekend 10:00 to 17:00

Switch(config)#time-range offlabfloor

Switch(config-time-range)#absolute start 00:00 01 January 2012 end 23:59 01 Jan 2012

Switch(config-time-range)#periodic weekdays 00:00 to 08:00

Switch(config-time-range)#periodic weekdays 20:00 to 23:59

Switch(config-time-range)#periodic weekend 00:00 to 10:00

Switch(config-time-range)#periodic weekend 17:00 to 23:59

Switch(config)#interface fastEthernet 1/0/3

!--- Configure a recurring event on the interface.

Switch(config-if)#energywise level 10 recurrence importance 80 time-range onlabfloor

Switch(config-if)#energywise level 0 recurrence importance 80 time-range offlabfloor

Switch(config-if)#energywise name IP_phone

Switch(config-if)#energywise role manager

Switch(config-if)#end

!--- Save the configurations in the device.

switch(config)#copy running-config startup-config

Switch(config)#exit

验证

使用本部分可确认配置能否正常运行。

命令输出解释程序（仅限注册用户）(OIT) 支持某些 show 命令。使用 OIT 可查看对 show 命令输出的分析。

请使用 show energywise 命令显示 EnergyWise 设置和状态。

例如：

Switch#show energywise

Module/

Interface   Role              Name                  Usage      Lvl   Imp  Type

---------   ----              ----                  -----      ---   ---  ----

access4lab1       Switch                45.0  (W)  10    80   parent

请使用 show energywise children 命令显示连接的终端的状态。

例如：

Switch#show energywise children

Module/

Interface   Role              Name                  Usage      Lvl   Imp  Type

---------   ----              ----                  -----      ---   ---  ----

access4lab1       Switch                45.0  (W)  10    80   parent

Fa1/0/3     IP Phone 7975     SEP0022905B90D4       12.0  (W)  10    1    PoE

Total Displayed: 2      Usage: 143.3

请使用 show energywise children provisioned 命令显示此交换机和已连接终端的 EnergyWise 信息摘要。

例如：

Switch#show energywise children provisioned

Module/

Interface   Role              Name                  Usage      Lvl   Imp  Type

---------   ----              ----                  -----      ---   ---  ----

access4lab1       Switch                45.0  (W)  10    80   parent

Fa1/0/1     interface         Fa0.5                 0.0   (W)  10    1    PoE

Fa1/0/2     interface         Fa0.5                 0.0   (W)  10    1    PoE

Fa1/0/3     IP Phone 7975     SEP0022905B90D4       12.0  (W)  10    1    PoE

Fa1/0/4     interface         Fa0.5                 0.0   (W)  10    1    PoE

<output truncated>

Total Displayed: 24     Usage: 139.9

请使用 show energywise domain 命令显示 EnergyWise 域信息。

例如：

Switch#show energywise domain

Name      : Switch

Domain    : Cisco

Protocol  : udp

IP        : 10.78.4.48

Port      : 43440

请使用 show energywise usage children 命令显示域成员和已连接终端的实际功率。

例如：

Switch#show energywise usage children

Interface   Name                     Usage      Caliber

---------   ----                     _____      _____

Switch                   45.0  (W)   max

Fa1/0/1     Fa1.0.1                  0.0   (W)   presumed

Fa1/0/2     Fa1.0.2                  0.0   (W)   presumed

Fa1/0/3     SEP0022905B90D4          12.0  (W)   trusted

Fa1/0/2     Fa1.0.4                  0.0   (W)   presumed

<output truncated>

Total Displayed: 24     Usage: 139.9

请使用 show energywise neighbors 命令显示此交换机的邻近表。

例如：

Switch#show energywise neighbors

Capability Codes: R - Router, T - Trans Bridge, B - Source Route Bridge

S - Switch, H - Host, I - IGMP, r - Repeater, P - Phone, U - Unknown

Id   Neighbor Name                 Ip:Port                 Prot   Capability

--   -------------                 -------                 ----   ----------

1                                  10.78.4.49:43440        static U

2    IP_phone A                    10.78.4.50:43440        udp    U

3    3560e-37-222                  20.1.2.222:6767         cdp    S I

请使用 show energywise level current 命令显示域成员的实际功率水平。当您使用 energywise level level recurrence importance importance time-range time-range-name 全局配置命令时，show energywise level current 的输出如下一个示例所示。

例如：

Switch#show energywise level current

Interface   Name                     Level  Value

---------   ----                     -----  -----

Switch                   10     45.0  (W)

请使用 show energywise recurrences 命令显示周期性事件的 EnergyWise 设置和状态。

例如：

Switch#show energywise recurrences

Id     Addr       Class Action Lvl Cron/Time-range

--     ----       ----- ------ --- ---------------

1      Fa2/0/3    QUERY SET    10  onlabfloor

2      Fa2/0/3    QUERY SET     0  offlabfloor

请使用 show energywise statistics 命令显示事件和错误的计数器。

例如：

Switch#show energywise statistics

Children:  2  Errors:  0  Drops:  31  Events:  102

相关信息

- Cisco Catalyst 3750 系列交换机支持页面

- 交换机产品支持

- LAN 交换技术支持

- 技术支持和文档 - Cisco Systems