Contents

Introduction

Prerequisites

Requirements

Componentes Utilizados

Conventions

Informações de Apoio

Configurar

Diagrama de Rede

Configurações

Verificar

Informações Relacionadas

Introduction

Este documento fornece um exemplo de configuração e verificação para os recursos do Cisco EnergyWise nos Catalyst 3750 Series Switches. Especificamente, este documento mostra como configurar os recursos do Cisco EnergyWise em um switch Catalyst 3750.

Prerequisites

Requirements

Certifique-se de atender a estes requisitos antes de tentar esta configuração:

- Ter conhecimento básico da configuração nos switches Cisco Catalyst 3750 Series

- Ter uma compreensão básica dos recursos do Cisco EnergyWise

Componentes Utilizados

As informações neste documento são baseadas nos Cisco Catalyst 3750 Series Switches.

The information in this document was created from the devices in a specific lab environment. All of the devices used in this document started with a cleared (default) configuration. If your network is live, make sure that you understand the potential impact of any command.

Conventions

Consulte as Convenções de Dicas Técnicas da Cisco para obter mais informações sobre convenções de documentos.

Informações de Apoio

O Cisco EnergyWise é um recurso de gerenciamento de energia que oferece a capacidade de monitorar e controlar a energia na infraestrutura de TI. O Cisco EnergyWise fornece uma estrutura pela qual a própria rede pode ser usada para abrir o gerenciamento de energia para todos os tipos de dispositivos.

Um domínio do Cisco EnergyWise é um agrupamento administrativo de dispositivos para fins de monitoramento e controle de energia. Os endpoints Cisco EnergyWise que oferecem suporte ao cliente EnergyWise SDK respondem a consultas EnergyWise iniciadas a partir de aplicativos de gerenciamento ou outros membros de domínio usando o protocolo Cisco EnergyWise.

Configurar

Nesta seção, você recebe as informações necessárias para configurar os recursos do Cisco EnergyWise descritos neste documento.

Nota:Use a Command Lookup Tool (somente clientes registrados) para obter mais informações sobre os comandos usados nesta seção.

Diagrama de Rede

Este documento utiliza a seguinte configuração de rede:

Configurações

Este documento utiliza as seguintes configurações:

Catalyst 3750 Switch

configure terminal

!--- Enable Cisco EnergyWise on supported platforms.

Switch(config)#energywise domain Cisco security shared-secret 0 cisco protocol

udp port 43440 ip 10.78.4.48

!--- Set the EnergyWise importance for the platform.

Switch(config)#energywise importance 80

!--- Set the EnergyWise keywords for the platform.

Switch(config)#energywise keywords lab1,lab2

Switch(config)#service password-encryption

!--- Enable communication between management applications which support EnergyWise protocol and domain.

Switch(config)#energywise management security shared-secret 7 070C285F4D06 port 60500

!--- Set the EnergyWise name for the platform.

Switch(config)#energywise name floor.lab

!--- Configure a static neighbor.

Switch(config)#energywise neighbor 2.2.4.31 43440

!--- Set the EnergyWise role for the platform.

Switch(config)#energywise role access4lab1

Switch(config)#energywise allow query save

!--- Configure Cisco EnergyWise on a port.

Switch(config)#time-range onlabfloor

Switch(config-time-range)#absolute start 00:00 01 January 2012 end 23:59 01 Jan 2012

Switch(config-time-range)#periodic weekdays 7:00 to 19:00

Switch(config-time-range)#periodic weekend 10:00 to 17:00

Switch(config)#time-range offlabfloor

Switch(config-time-range)#absolute start 00:00 01 January 2012 end 23:59 01 Jan 2012

Switch(config-time-range)#periodic weekdays 00:00 to 08:00

Switch(config-time-range)#periodic weekdays 20:00 to 23:59

Switch(config-time-range)#periodic weekend 00:00 to 10:00

Switch(config-time-range)#periodic weekend 17:00 to 23:59

Switch(config)#interface fastEthernet 1/0/3

!--- Configure a recurring event on the interface.

Switch(config-if)#energywise level 10 recurrence importance 80 time-range onlabfloor

Switch(config-if)#energywise level 0 recurrence importance 80 time-range offlabfloor

Switch(config-if)#energywise name IP_phone

Switch(config-if)#energywise role manager

Switch(config-if)#end

!--- Save the configurations in the device.

switch(config)#copy running-config startup-config

Switch(config)#exit

Verificar

Use esta seção para confirmar se a sua configuração funciona corretamente.

A Output Interpreter Tool ( somente clientes registrados) (OIT) oferece suporte a determinados comandos show. Use a OIT para exibir uma análise da saída do comando show.

Use o comando show energywise para exibir as configurações e o status do EnergyWise.

Por exemplo:

Switch#show energywise

Module/

Interface   Role              Name                  Usage      Lvl   Imp  Type

---------   ----              ----                  -----      ---   ---  ----

access4lab1       Switch                45.0  (W)  10    80   parent

Use o comando show energywise child para exibir o status do ponto final conectado.

Por exemplo:

Switch#show energywise children

Module/

Interface   Role              Name                  Usage      Lvl   Imp  Type

---------   ----              ----                  -----      ---   ---  ----

access4lab1       Switch                45.0  (W)  10    80   parent

Fa1/0/3     IP Phone 7975     SEP0022905B90D4       12.0  (W)  10    1    PoE

Total Displayed: 2      Usage: 143.3

Use o comando show energywise child provisioned para exibir um resumo das informações do EnergyWise para o switch e os terminais conectados.

Por exemplo:

Switch#show energywise children provisioned

Module/

Interface   Role              Name                  Usage      Lvl   Imp  Type

---------   ----              ----                  -----      ---   ---  ----

access4lab1       Switch                45.0  (W)  10    80   parent

Fa1/0/1     interface         Fa0.5                 0.0   (W)  10    1    PoE

Fa1/0/2     interface         Fa0.5                 0.0   (W)  10    1    PoE

Fa1/0/3     IP Phone 7975     SEP0022905B90D4       12.0  (W)  10    1    PoE

Fa1/0/4     interface         Fa0.5                 0.0   (W)  10    1    PoE

<output truncated>

Total Displayed: 24     Usage: 139.9

Use o comando show energywise domain para exibir as informações de domínio do EnergyWise.

Por exemplo:

Switch#show energywise domain

Name      : Switch

Domain    : Cisco

Protocol  : udp

IP        : 10.78.4.48

Port      : 43440

Use o comando show energywise usage child para exibir a potência real do membro do domínio e dos terminais conectados.

Por exemplo:

Switch#show energywise usage children

Interface   Name                     Usage      Caliber

---------   ----                     _____      _____

Switch                   45.0  (W)   max

Fa1/0/1     Fa1.0.1                  0.0   (W)   presumed

Fa1/0/2     Fa1.0.2                  0.0   (W)   presumed

Fa1/0/3     SEP0022905B90D4          12.0  (W)   trusted

Fa1/0/2     Fa1.0.4                  0.0   (W)   presumed

<output truncated>

Total Displayed: 24     Usage: 139.9

Use o comando show energywise neighbors para exibir a tabela de vizinhos do switch.

Por exemplo:

Switch#show energywise neighbors

Capability Codes: R - Router, T - Trans Bridge, B - Source Route Bridge

S - Switch, H - Host, I - IGMP, r - Repeater, P - Phone, U - Unknown

Id   Neighbor Name                 Ip:Port                 Prot   Capability

--   -------------                 -------                 ----   ----------

1                                  10.78.4.49:43440        static U

2    IP_phone A                    10.78.4.50:43440        udp    U

3    3560e-37-222                  20.1.2.222:6767         cdp    S I

Use o comando show energywise level current para exibir os níveis de potência reais para o membro de domínio. Quando você usa o comando de configuração global energywise level level frequency importante time-range time-name , a saída do comando de configuração global show energywise level current é mostrada no próximo exemplo.

Por exemplo:

Switch#show energywise level current

Interface   Name                     Level  Value

---------   ----                     -----  -----

Switch                   10     45.0  (W)

Use o comando show energywise recurrences para exibir as configurações e o status do EnergyWise para o evento recorrente.

Por exemplo:

Switch#show energywise recurrences

Id     Addr       Class Action Lvl Cron/Time-range

--     ----       ----- ------ --- ---------------

1      Fa2/0/3    QUERY SET    10  onlabfloor

2      Fa2/0/3    QUERY SET     0  offlabfloor

Use o comando show energywise statistics para exibir os contadores de eventos e erros.

Por exemplo:

Switch#show energywise statistics

Children:  2  Errors:  0  Drops:  31  Events:  102

Informações Relacionadas

- Página de suporte dos switches Cisco Catalyst 3750 Series

- Suporte ao Produto - Switches

- Suporte de tecnologia de switching de LAN

- Suporte Técnico e Documentação - Cisco Systems